Planning and DesignPlanning and design
The overall plan design of the factory laboratory shall meet the requirements of scientific experimental work, and the planned area index shall be implemented in accordance with the "Planned Area Index of Scientific Research and Construction Projects". It should include the layout and vertical design of various types of houses, outdoor experimental sites and roads, the comprehensive design of public facilities pipeline networks, and environmental design. The original terrain, landform, features, water surface and space of the base and the existing public facilities should be reasonably used. All types of housing should be arranged in a centralized manner so that the functional zones are clear, the layout is reasonable, the connections are convenient, and they do not interfere with each other, and there is room for development. Guangdong Renfeng Industry , a laboratory total solution provider!
Consulting Tel: 15813385418
Dwellings should not be built in scientific experimental areas. When built in the same area, they shall be separated from each other, with separate entrances and exits, and shall comply with relevant regulations on pollution prevention and interference.
The position of independent buildings or structures using radioactive, explosive, toxic and polluting substances in the general plane shall comply with relevant safety, protection, evacuation and environmental protection regulations.
The location of public facilities in the general plane shall meet the requirements of energy conservation and environmental protection. Substations and freezing stations should be located near the center of the load with minimal interference to the surrounding environment. When scientific experiment work requires vibration isolation, it should be arranged according to its vibration isolation distance. When vibration isolation distance cannot be guaranteed, necessary vibration isolation measures should be taken.
Factory laboratory construction-laboratory fire protection system
The laboratory is a special environment, and the requirements for fire protection are much higher than ordinary office buildings. The laboratory design should adopt different fire protection measures to ensure the fire safety of the laboratory according to the specific conditions of the laboratory (equipment investment and process characteristics, experimental process requirements, types of stored samples and reagents, characteristics of laboratory buildings, etc.). For precision equipment rooms, aseptic rooms, power distribution rooms, and uninterruptible power supply rooms, automatic sprinkler devices cannot be used for fire protection. Instead, gas fire extinguishing devices should be used to prevent the automatic sprinkler devices from damaging instruments or destroying cleanliness. surroundings.
Factory laboratory construction-laboratory water supply and drainage system
The pipes of the drainage system should be resistant to acid and alkali corrosion and the melting of organic reagents. PPR or other materials should be used instead of ordinary PVC pipes. At the same time, it should be based on the nature, flow, and discharge of sewage and the outdoor drainage conditions. set a strategy. Due to the complexity of large-scale laboratory sewer pipes, it is necessary to take necessary measures to avoid pipeline blockage and leakage, such as developing good water habits, placing filters, setting water traps, and connecting elbows at 45 ° angles. The centralized water supply system is not recommended due to its higher cost and unstable water quality. In order to avoid secondary pollution, an inductive faucet can be used. The disadvantage is that it is easy to break.
Guangdong Renfeng Industrial Co., Ltd. is currently one of the few domestic laboratory solution providers. The company has a professional design team, a nationwide construction team, and highly competitive laboratory furniture products. The company specializes in laboratory planning and design, laboratory furniture production and installation engineering, laboratory ventilation and purification engineering, laboratory professional equipment consumables sales, laboratory information management system construction and other services.